National Electrical Code Top Ten Tips: Article 320 through Article 340 -- Cables
Based on the 2020 NEC
by Mark Lamendola
Please note, we do quote from copyrighted material. While the NFPA
does allow such quotes, it does so only for the purposes of education
regarding the National Electrical Code. This article is not a substitute
for the NEC.
These are the 10 NEC Article 320 through NEC Article 340 items we deem
most important, based on the pervasiveness of confusion and the
potential costs of same.
- NEC Article 320 through 340 contain the requirements for various
types of cable. Remember that, and your life will be much easier.
- Each Article in this series provides the uses permitted and the
uses not permitted. At one time, you had to hunt for where each article listed these. Now you will find them in subsection 10 and 12, respectively.
- Article 320 presents requirements for type AC: Armored Cable.
This kind of cable has a metallic jacket. While many people assume
it's the most durable of all cables and can be used anywhere, this
is not true.
- Article 322 and Article 324 address two types of flat cable
assembly. Only one of them is designed for use under carpet squares.
- Article 326: You cannot use Integrated Gas Spacer Cable (Type IGS)
inside buildings. This makes sense when you think about it. What happens if it leaks?
- Article 328 provides the requirements for Medium Voltage Cable
(Type MV). You cannot use it on systems above 35 kV (35,000
- Article 330 provides the requirements for Metal-Clad Cable (Type
MC). Note, this differs from armored cable. Article 332 provides the requirements for Mineral Insulated, Metal-Sheathed Cable, Type MI.
- Article 334 provides the requirements for various kinds of
Non-Metallic Sheathed Cable (Types NM, NMC, and NMS). Article 336 provides the requirements for Power and Control Tray Cable, Type TC.
- Article 337 covers Type P Cable. Article 338 provides the requirements for Service Entrance Cable
((Type SE and Type USE).
- Article 340 provides the requirements for Underground Feeder and
Branch-Circuit Cable (Type UF).
The other NEC Articles from this point forward to the end of NEC
Chapter 3 are short, and each is specific to a type of raceway.